Summary:Electrical Circuits Question: i am hooking increase a tan bed. Follow to the instructions, the operates indigenous a 220 AC source.

You are watching: How to wire a tanning bed

## How to install a tanning Bed Circuit

Installing a tanning Bed Circuit ns am hooking up a demorphs bed. Follow to the instructions, the operates native a 220 AC source. It calls for a 6-20R outlet and a dedicated 20 amp circuit. I have actually ran the 12/2 v ground wire. I"ve installed the outlet. That pipeline the breaker. From mine somewhat minimal knowledge, i assumed I need a 2 pole 20 amp breaker. The dashboard is a Zinsco. i was may be to discover the breakers online and also purchased a R38-20 (2 X 1Pole 20Amp 120/240V breaker). The R collection matches the other skinny breakers currently being used. Inside the dashboard I connected the ceiling copper wire to the soil bar and also the white and black come the breaker.
 After hooking everything up and transforming on the demorphs bed, one next of the breaker trips after about 10 seconds. I am beginning to wonder if the breaker is wrong. Ns am reasoning its no an actual 2 pole breaker, but a twin single pole. This would make a difference, Right? Thanks- Tim N. Hi Tim - great Electrical fix Question! The Zinsco R38-20 breaker should carry out 240 volts if the relationships on the bottom the the breaker space staggered where they will certainly come into link with opposing busses in the panel. This method that one next of the twin breaker will affix to among the busses the the panel and the various other will next of the breaker will affix with the various other buss of the panel which would develop 240 volts. It"s always best to inspect the voltage source at the breaker prior to attaching the wires come make sure of her voltage. This have the right to be done through a tester capable of reading 240 Volts AC and also connecting the 2 leads to the terminal screws ~ above the breaker. It is constantly a great idea to check terminal to terminal which should produce 240 volts, and also then every terminal come ground to verify 120 volts. Once the voltage is verified make certain the wires room inside the terminals all the way. The pair Zinsco breakers have a very tiny area come insert the wire and it have the right to be tricky to obtain the cable all the means inside the terminal. Let me recognize what girlfriend find. From: Tim N. Dave, The breaker does have the staggered contacts and also I have actually the relationships all the means in the terminals. So i cant number why that is not working I go ask the human who marketed it come me and his email an answer was just PUT IN THE very same THING (WIRE and so on .)BUT through THE 2 POLES! What else carry out you think it can be? thanks Tim. Hello Tim - If girlfriend are giving the specified power to the tan bed and also the circuit is tripping then there may be a problem internally through the tanning bed. To uncover out what the is would involve a process of elimination, such together disconnecting one component at a time. However if the unit is brand brand-new you might be voiding your warrantee. In that case I would contact the provider and also ask because that a instead of or some form of resolution. Because the circuit is not tripping automatically this would not show a straight short, for this reason I think there might be a component the is not right. With most tanning bed there aren"t very many components, mostly the lights, fan and timer, however there might be a difficulty with one of these components. Have you made a voltage check to ground and also terminal to terminal? From: Tim N. No I have not checked the volts. I am away from the panel, so i can"t in ~ this time. Ns will and also report earlier to you. It may be awhile as its a project I to be doing because that my girl friend out of state. She resides in a condo and also the the breaker crate looks pretty conventional to me. She did have actually an electrician look at it prior to I got associated to make certain that the organization would manage the included circuit and also he claimed it would. I have included circuits before without any issue in my house and thought i can handle this.Thanks because that the follow-ups. Tim

## Electrical Wiring Tips for Home electric Wiring Projects

Tripping Circuit Breaker, Outlet at a wall Switch, irradiate Fixture there is no a ground Wire, help with Home electric Wiring Projects.

## Basic Home electric Wiring by Example

 »You deserve to Avoid i have lot of money Mistakes!«Here is just how to carry out It:Wire It ideal with the assist of my portrayed Wiring BookGreat for any Home Wiring Project.

## Complete guide to Home electric Wiring

Perfect for Homeowners, Students,Handyman, Handywomen, and ElectriciansIncludes:Wiring GFCI OutletsWiring Home electric Circuits120 Volt and 240 Volt Outlet CircuitsWiring light SwitchesWiring 3-Wire and 4-Wire electrical RangeWiring 3-Wire and 4-Wire Dryer Cord and also Dryer OutletHow come Troubleshoot and also Repair electrical WiringWiring approaches for Upgrading electrical WiringNEC Codes because that Home electric Wiring....and lot more.

## Electric Circuit Problem

Electrical Circuit Wiring Articles220 Volt come 110 Volt Wiring220 Volt Heater Wiring Circuit220 Volt to 120 Volt CircuitDryer Circuit WiringLightning Damaged Wiring Circuit120 Volt Heater CircuitInstalling melted Wiring CircuitKitchen Wiring Circuit not WorkingWelder Circuit WiringRange and also Dryer Circuit WiringRefrigerator Circuit WiringRemote security Circuit WiringRoof Circuit Conduit WiringSquare D Circuit BreakersStorage Unit Circuit WiringSwimming swimming pool Circuit WiringTanning Bed Circuit WiringWasher and Dryer Circuit WiringOven Circuit Voltage FeedbackWater Heater Circuit WiringWater Heater Tripping Circuit BreakerWire size for a Microwave CircuitWiring a Microwave CircuitWorkshop electric Circuit Wiring

### Electrical Wiring and also Electrical Repairs

Skill Level:Intermediate to progressed - electrical Repairs and Circuit Wiring is ideal Performed through a Licensed electrical Contractor.Tools Required:Basic Electricians bag of Hand Tools, a Voltage Tester and also a Multi Meter.Estimated Time: Depends on personal level experience, capability to work with tools, occupational with electric wiring, and also the available access to the task area.Precaution: recognize the job circuit, turn it OFF and Tag it v a Note prior to working through the wiring.Important: modifying existing electric circuits or installing added electrical wiring should be excellent according come local and also national electrical codes with a permit and be inspected.
 Learn electric WiringInstructional electrical Wiring Videos
 » how To wire It RIGHT!«Wire it with Confidence!Fully IllustratedInstant DownloadNow you CanWire it favor a Pro!

## Recent Testimonials

I think your site offers the the clearest and also best electrical information for homeowners ns have ever before seen on the net.You have offered me confidence to perform my own projects which ns never had before. Say thanks to YOU!Paul, native Foxboro, Massachusetts i wish I uncovered this website earlier, that is by much the ideal electrical related source I have uncovered on the web.George, indigenous Scranton, Pennsylvania ns love this website for an office worker that does not understand anything about electric wiring.

See more: Are Guinea Pigs Nocturnal Or Diurnal, Are Guinea Pigs Nocturnal Animals

Bill, from brand-new York City, brand-new York This website is so much better than the 3 publications I just bought, i wish i came here first.Collin, from grand Rapids, Michigan say thanks to you for answering mine question.I to be able to acquire this done. This site is perfect. Ns am happy I discovered it. Please store it going. Mike, from Chicago, Illinois

### Help with home Wiring

Troubleshooting electric WiringUsing electric Testers and MetersHome electric SafetyHome construction SafetyElectrical Calculations and FormulasHome electrical Codes for house WiringElectrical Wiring Questions

### Wiring Parts and also Tools

Electrical BoxesElectrical WireElectrical ToolsTesters and also Meters

### Home electric Directories

Electrical write-ups DirectoryWiring Diagrams DirectoryDIY electric Wiring DirectoryDIY electrical ArticlesElectrical write-ups Category DirectoryRecent electric Questions and AnswersElectrical Repair short articles Listing

### Electrical Wiring Resources

License codes & home ConstructionElectrician Training and CertificationElectrical Wiring ResourcesElectrical SuppliersElectrical advice NewsletterFree electric HelpHome electrical Wiring collection Home electric Wiring VideosElectrical power Videos